The WASP2 series product is an all-in-one logger and cellular telemetry unit with internal batteries that can last up to 5 years.
It is designed to connect directly to many types of meters & sensors. The meters & sensors supported by your WASP2 will be determined by its connector types as specified in the full product code. See diagram below to find your Outpost full product code.
To get your WASP2 up and running, follow these steps below to make connections, setup the website and then test the connection.
Step 1 - Activate your WASP2
Before heading out to site, confirm that your WASP2 is connecting to Outpostcentral.com and that it's visible in your login:
Step 2 - Make connections
The WASP2 has up to 2 connectors for meter/sensor connections, depending on the product code. Click on the links in the table below for the detailed wiring for the connection type of your WASP2.
|Product Code Option (description)
|Product options with M12 style connectors
ENV (General Environmental, 1 x counter & 1 x 4-20mA)
SDIM12 (SDI12 interface)
|Product options with "flying lead" connections
FL (Flow, Leaded)
ML (Milliamp, Leaded)
Step 3 - Confirm website connection
Once connections are made on site, re-activate the Outpost and confirm it can sucessfully connect in the local cellular coverage environment by checking the it has connected since being activated at site.
Step 4 - Setup Outpost site details and input calibrations
Setup site details including site name, project reference in the website: Managing Sites
Setup input calibrations for counter, 4-20mA, SDI12, MODBUS or other input types in the website: Setting Inputs
Step 5 - Confirm data is as expected
After setting up the desired calibrations, re-activate the Outpost to send the new settings down, and then activate one final time to cause calibrated readings to be read and uploaded to the website (all inputs configured to log are forced to read upon an activation).